“Best of IWC”
The Best of IWC Webinar Series is a great way to preview the high quality technical content presented at the International Water Conference®.
- Attendees can earn 1 PDH credit from the comfort of their own computer.
- It is FREE to attend, but registration is required for pdh certification. Multiple viewers on one computer will be required to sign in on the required form distributed at the webinar.
Note: Individual NY P.E.’s requesting the 1 PDH must sign into the webinar via the link provided when registered and are also required to sign a login sheet after completion of the webinar. NY P.E.’s attending the webinar as a group require only one person to register for the webinar. That person is the room moderator for the group and must sign into the webinar via the link provided when registered. Each attendee in the group will be required to sign in and out on the login sheet. The times and signatures are verified by the room moderator.
Topic: Boiler Water — Register Here
Tuesday, March 17, 2020 — Noon – 1:00pm EST
Peter Meyers, ResinTech Inc., West Berlin, NJ
IWC 19-02: The Death of Deep Bed Condensate Polishing
With the ever-expanding capacity of solar and wind power, most thermal power plants are now cycling rather than operating continuously at full power. Cycling dramatically increases the transport of corrosion products and increases both corrosion and metal fatigue. Recent EPRI guidelines for combined cycle plants is to operate at elevated condensate pH, at least 9.6 and preferably 9.8 to 10.0. Although other types of power plants have lower pH guidelines, there is a general push at many older plants that do not have high chrome metallurgy to operate at higher pH as a way of minimizing FAC. The increase in amine (or ammonia concentration) makes condensate polishing more difficult and in some cases spells death for Deep Bed Condensate Polishers.
Deep bed polishers perform several roles including crud removal, fast clean up and minimal time required to reach full power following outages and perhaps most importantly (at least for deep beds), the ability to maintain low levels of sodium, chloride and sulfate, with minor cooling water leaks. However, as condensate pH increases, the polishers exhaust more rapidly. Above a pH of much above 9 it is virtually impossible to regenerate the polishers fast enough to stay in service, at least with the polisher resins in the H/OH form. Ammonia (or amine) form operation is possible with advanced external regeneration systems but beyond a pH of approx. 9.6, the preference of the IX resins for sodium drops to the point where there is no longer any capacity to remove sodium from the incoming condensate. At best, the polishers don’t add sodium. At worst, deep bed polishers become a primary source of sodium.
In this paper we present both theoretical arguments and operating experience from several power plants that operate deep bed condensate polishers. The bottom line is that new power plants are less likely to include deep bed polishers. Instead they will change metallurgy, improve condensers and use powdered fiber type precoat filters for crud removal and various powdered resin mixtures for start-up. And what is arguably the most complex ion exchange system ever devised may well join the dinosaurs, dodo’s and floppy discs, in the annals of extinction.
Ken Kuruc, Hach, Loveland, CO
IWC 19-03: On-Line Iron Studies using a Film Forming Product and a Film Forming Amine
Film forming products (FFP) and film forming amines (FFA) continue to receive attention as a means of passivating metal surfaces in the steam cycle, especially with systems that cycle frequently. Facilities that have added these products to their cycle need to prove that their investments are effective in reducing both production and transport of corrosion products.
In two separate studies, one using a FFP and the other a FFA, a laser nephelometer is employed along with a laboratory spectrophotometer to quantify on-line concentrations of iron on a continuous basis in the steam cycle. Before and after results will be shared with respect to corrosion product transfer on a real time basis. Data will be shown as the plants progress through conditions such as repetitive load changes and cycling, when corrosion of an untreated surface can be most prevalent. The protective capacity for the specific product utilized will be observed over time to demonstrate its contribution in reducing corrosion product and its transport throughout the steam cycle. Finally, the difference in performance between the FFA and FFP will be discussed.
Topic: ZLD — Register Here
Thursday, April 30, 2020 — Noon-1:00pm EST
Travis Reynolds, GE Power, Knoxville, TN; Cuong Pham, Evergy, Weston, MO
IWC 19-05: Iatan SDE Design, Operation, Maintenance and Operational Costs
After two years of successful operation, performance & emissions compliance, and greater than ninety-eight percent availability, the operating experiences and costs associated with the SDE have been quantified. This paper and presentation will discuss the SDE design approach, operation and maintenance experiences, and costs that have been observed over the past two years of operation.
Josh Dewanaga P.E., and David Ciszewski, SUEZ Water Technologies & Solutions, Bellevue, WA; David Rowe, SUEZ Water Technologies & Solutions, Norfolk, VA; Lauren Barbir, SUEZ Water Technologies & Solutions, Trevose, PA
IWC 19-06: Integrated Water and Wastewater Zero Discharge System for Liquefied Natural Gas Plant: Lessons Learned from Design, Start-Up and Operations
When tackling the daunting task of expanding an existing liquefied natural gas (LNG) plant and managing water demands in an environmentally sensitive area, what are the critical decisions when selecting the design and operational support model for your water and wastewater systems? For a LNG terminal on the East coast, the journey to full operations of its expansion project started six years earlier with the owner evaluating water needs and requirements for the environmental impact in the area. The decision was to select a high recovery water treatment system and a zero liquid discharge system to minimize both water withdrawal and environmental impact. The LNG plant owner (who is also the operator) and EPC firm selected a single company to design the two systems which became one integrated system. This decision proved efficient for both design and start-up phases. When evaluating the operational support model, the resulting decision was to outsource the operations and maintenance to the same company designing the integrated water system. This paper discusses notable events and learnings from design, start-up/commissioning, and first year of operations.
Topic: Mining — Register Here
Thursday, May 21, 2020 — Noon-1:00pm EST
Jonathan Witt, P.E. and Alan Prouty, J.R. Simplot Company, Boise, ID; Jeremy Aulbach, P.E., Brown and Caldwell, Boise, ID
IWC 19-17: Physio-Biological Removal of Selenium from Mining Impacted Waters
The Smoky Canyon Mine owned by the J.R. Simplot Company constructed the Hoopes Selenium Treatability Study Pilot (Hoopes TSP), which implemented physical and biological treatment to evaluate operational performance of active selenium water treatment from mine-impacted waters. The Smoky Canyon Mine is located within the Idaho Phosphate District, which is rich in sedimentary phosphate ores that are found concurrent with selenium-bearing deposits. Past mining practices have led to elevated levels of selenium in the mine-impacted waters. The physical and biological treatment processes applied include UF, RO, anaerobic biological, and aerobic biological. While these established technologies are routinely applied individually in water treatment, these technologies were applied in an innovative arrangement that shows significant promise in its application to remove selenium from mine-impacted waters. Total selenium concentrations of the mine-impacted waters fed to the Hoopes TSP averaged 0.144 mg/L during the study period presented. Hoopes TSP effluent total selenium concentrations averaged 0.015 mg/L during the study period presented. Details of the mine setting, influent water parameters, treatability study pilot system configuration, and initial 20 weeks of operational results are presented in this paper.
Alex Drak, Roi Zaken Porat and Tomar Efrat, IDE Technologies, Kadima, Israel; Marco Kerstholt, Royal HaskoningDHV, South Africa; Gerald van Houwelingen, Royal HaskoningDHV, Netherlands
IWC 19-20: Mine Impacted Water Minimization Technology – 3 Years of Development
A significant amount of water is used in the mining process, and it is often necessary to treat this water, which is characterized by neutral to low pH and moderate to high total dissolved solids content. Sulfate anions, typically present in this water, are introduced largely as a result of partial oxidation of sulfide-bearing ores (often containing pyrite). Calcium cations are also usually present in water as a result of partial dissolution of dolomitic compounds present in the waste rock. These two ions, with combined concentration close to the gypsum saturation limit, make the treatment process of mine impacted water relatively challenging.
Currently, mine impacted water is usually treated by adding lime to neutralize the acid and precipitate heavy metals as hydroxides. After partial acidification, the effluent from this process is recycled or discharged to the receiving environment. Depending on the pH targeted in the neutralization step, this effluent can still contain a relatively high concentration of sulfate and calcium. Increased concern led to the introduction of recommended guideline values for the sulfate concentration in the discharged effluent. Based on World Health Organization (WHO) guidelines, the recommended values for the sulfate concentration are generally below 500 mg/L.
The demand to produce water with sulfate concentration in the 250 – 500 mg/L range poses a technological challenge not yet sufficiently addressed. Therefore, it is necessary to develop new technologies to address these challenges. A recently developed technology, MaxH2O Desalter, containing an RO system with an integrated salt precipitation unit, makes it possible to achieve the required sulfate concentration. This paper presents the results of a 3 year development process of the MaxH2O Desalter technology. Different types of mine impacted water, collected from different mine sites, were treated. The results show that the system can reach recoveries of over 85%, at which the calcium sulfate saturation index theoretically reaches over 1,000%, which could lead to sudden
calcium sulfate precipitation on the RO membrane. In practice, in the MaxH2O Desalter process, the calcium sulfate saturation index was maintained in the range of 200% – 400%, by continuous precipitation of carbonate and sulfate compounds in the integrated salt precipitation unit. The system operated without the addition of chemicals other than antiscalant and calcium carbonate seeds and produced pellets with more than 90% dry solids content, which did not require further sludge dewatering treatment. These results show the significant advantage of the developed system as a treatment alternative for mine impacted water. The developed system saves operational costs compared to current sulfate reduction technologies by decreasing chemical consumption and decreasing the amount of sludge to be discharged, with competitive investment costs given the high water recovery that can be achieved in this new process. If the produced brine were to be treated (e.g., using a high-density sludge treatment process) a very significant reduction in total dissolved solids in the finally discharged water (upon blending the treated brine with permeate) could be realized.
Topic: Industrial Wastewater — Register Here
Tuesday, June 18, 2020 — Noon – 1:00pm EST
Brian Moore, Ph.D., Arcadis, Clifton Park, NY
IWC 19-26: Advanced Wastewater Recycle at an Automotive Plant in Silao, Mexico
A major automotive manufacturer manufactures engines, transmissions and full-size trucks at a large manufacturing complex in Silao, Guanajuato, Mexico. The Site employs approximately 6,000 personnel. Additionally, there are approximately 4,000 contracted employees on site in any given day. The site has experienced dramatic growth and is currently under construction to add nearly 3 million square feet of new production facilities.
For all freshwater the Site relies on six groundwater wells, which they must frequently rotate (in/out of service) to obtain the water needed for manufacturing operations. In addition to very high taxes for groundwater extraction, the aquifer levels are declining; the aquifer has been identified as stressed and the region is expected to have continued growth in population, agriculture and industry (World Bank, 2004). As such, the aquifer cannot provide the additional 30-40% water required following the plant expansion.
Considering its environmental goals, the status of the region and aquifer and to reduce production disruption risk, the automotive manufacturer has embarked on a comprehensive water recycling program to maximize water reuse for manufacturing processes.
An array of concepts for treatment and recycle were developed and vetted relative to key project criteria (e.g. percent of wastewater recycled, robustness, operability, CapEx and OpEx, etc). The treatment train selected for this new water recycle system includes a membrane bioreactor (MBR) and two-stage reverse osmosis (RO) in Phase I; the performance/operability of these processes benefit from strategic upstream and waste segregation components to the project. A future phase of the project would include on- site treatment of the brine from the RO process, recovering even more water through application of zero-liquid discharge technology (evaporator/ crystallizer combination with mechanical vapor recompression).
During this IWC presentation, we intend to walk the audience through the entire process for Phase 1 of the project, including feasibility assessment, water and constituent mass balance, concept development and refinement, design, construction and start-up (on-line Feb 2019). We will also discuss Phase II of the project.
Mark Knight and Nicolas Hameon-Denis, SUEZ Water Technologies & Solutions, Oakville, ON, Canada; Shane Lund, SUEZ Water Technologies & Solutions, Trevose, PA; Jordan Schmidt, Brad McIlwain and Shawn Watkins, LuminUltra Technologies Ltd., Fredericton, NB, Canada
IWC 19-57: How Hot is Too Hot? Reviewing the Treatment Performance of Refinery WWTP Biological Treatment Systems Operating at High Temperatures
This study reviews the treatment performance and microbial ecology of two North American refinery WWTP biological treatment systems which continuously operate between 38°C to 52°C. Results from both refinery WWTP’s show that biological treatment systems can effectively remove organic compounds and nitrify ammonia above 35°C which can provide certain advantages when optimizing an industrial WWTP, upgrading upstream processes or building a new green field plant.
Topic: Reverse Osmosis — Register Here
Thursday, July 23, 2020 — Noon-1:00pm EST
Rich Franks, P.E., Alexandra Rubin and Craig Bartels, Ph.D., Hydranautics, Oceanside, CA; Peter Cartwright, P.E., Cartwright Consulting Co., Minneapolis, MN
IWC 19-33: The Contrarian Use of Chlorine to Control Biofouling in RO Membranes
It is well known that the reverse osmosis membrane’s polyamide chemistry is incompatible with chlorine. This limitation of the polyamide chemistry is sometimes referred to as the Achilles Heel of RO membranes. In many RO systems, the absence of a continuous biocide such as chlorine leads to extreme biofouling, rapid performance degradation, frequent cleanings, extended downtime and shortened membrane life. However, regardless of this stated incompatibility, there does exist a low level of tolerance before damage to the molecular structure of the membrane causes a noticeable change in RO performance. This tolerance, which is affected by a number of variables, has gradually increased over the years as the membrane chemistry has evolved. Today’s membranes are more highly crosslinked than those of previous generations. These latest chemistries result in lower pressures and better rejection; including better rejection of more challenging constituents such as silica and organics. These better chemistries have the added benefit of being more robust and, therefore, more chemically tolerant. This includes improved tolerance, not only to caustic or acid cleanings, but also to chlorine. Though no membrane supplier promotes these membranes as chlorine tolerant, their improved durability makes the use of chlorine to control biofouling an option worth considering when confronted with extreme biofouling. At least one RO plant is experimenting with intermittent exposure to low levels of chlorine for the purpose of managing biofouling. After a biofilm is allowed to build on the membranes, as evidenced by decreasing permeability and increasing differential pressure, periodic chlorine dosing is initiated. Though the chlorine improves membrane performance, the permeability and differential pressures do not return to their original, baseline values; the intention being to minimize chlorine exposure and maintain some foulant as a protective layer. This paper will present the chemistry behind past and current chlorine limitations. RO membranes exposed to chlorine in the laboratory will be analyzed. The RO system operating data, both before and during chlorine dosing, will also be presented. Analysis of elements extracted from the RO system will be shared in order to further characterize the membrane performance and chemistry after “real world” chlorine exposure.
Elke Peirtsegaele, MICRODYN-NADIR, Goleta, CA
IWC 19-36: Innovative Spiral-Wound Membrane Elements for High Temperature Desalination Applications
Water desalination has become one of the most important methods of alleviating water shortages and meeting stricter environmental regulations across the world. While spiral-wound reverse osmosis (RO) and nanofiltration (NF) membrane elements have proven very successful in a variety of desalination applications, more and more applications are emerging that require spiral-wound membrane elements capable of handling high temperatures or extreme cleaning conditions. Because industry-standard RO and NF water elements are limited to a maximum operating temperature of 45°C (113°F), membrane manufacturers are investigating alternative materials to build high temperature elements for applications where standard RO and NF elements cannot be used.
This paper explains how data is used to determine when more robust element components (i.e. materials of construction) such as feed spacers, permeate carriers, permeate tubes and outerwraps are needed to develop elements that can handle different levels of elevated temperatures. Elements constructed with these alternative materials fall into four categories based on temperature tolerance:
- Warm temperature operation (up to 60°C continuous)
- High temperature operation (up to 80°C continuous)
- Heat-sanitization (sanitization up to 90°C)
- Extreme cleaning at high pH and high temperature (up to pH 13 and 75°C)
Overall, this paper focuses on why high temperature spiral-wound elements are needed, which applications require these types of elements and how different element components can be combined to tackle an even broader range of applications than ever before.
As an offering of the high quality technical content presented at the IWC, please review these historical papers from IWC-past. Technical Papers from more recent conferences, and our archived history, can be found here. Check back often, as content will be updated on a regular basis.
Please click on title to download paper
IWC 95-02: A COMPARISON OF A SELECTIVE RESIN WITH A CONVENTIONAL RESIN FOR NITRATE REMOVAL
G.L. Dimotsis, Sybron Chemicals Inc., Birmingham, NJ
F.X. McGarvey, Sybron Chemicals Inc., Birmingham, NJ
IWC 09-36: Steam Generation Using Produced Water: Lessons Learned
Martin R. Godfrey, Nalco Company, Naperville, Illinois
Keywords: Produced Water, OTSG, Evaporator, Steam Generation, SAGD
IWC 07-24: Equipment Design Considerations for Lime and Ion Exchange Treatment of Produced Water in Heavy Oil Extraction
Robert Holloway, Holloway Associates, Etobicoke, Ontario, Canada
Gordon Page, Page Technology Ltd., Calgary, Alberta, Canada
Prepared Discussion for IWC 07-24:
John E. Fair, P.Eng., Fair Canada Engineering Ltd., Calgary, Alberta
Author’s Closure for IWC 07-24:
Robert Holloway, Holloway Associates, Etobicoke, Ontario, Canada
Gordon Page, Page Technology Ltd., Calgary, Alberta, Canada